|BX-DM1/E -10, -18, -36, -M Firmware Revision History|
|.GA File Version
|.OS File Version
Description of Problems / Additions / Changes
|2.6.2||14 Aug 2019||
Setup TCP/IP Parameters (SETUPIP) can now set the IP address for the DNS
BRX-M CPU now properly handles Timed Interrupts.
|1.0.6||2.6.1||19 Jun 2019||
Added support for the
|1.0.5||2.5.2||27 Mar 2019||
Added support for the following modules:
Fixed a problem that would cause the Modbus/TCP server to fail if the
client impropertly requested more than 125 words in a single request.
|2.3.2||30 Aug 2018||
Fixed a problem that caused the BX-04ADM-1 and BX-06RTD to not work properly in a BX-DMIO or BX-EBC100 when being controlled by the Ethernet I/O Master.
Fixed a problem in the BX-DM1E-M where the I/O System View was reporting the wrong slot number for I/O module errors.
Fixed a problem that prevented analog and temperature inputs from always reporting broken transmitter errors. Now any time a current or temperature input is enabled and there is no probe attached, the associated X bit will be ON and a Warning (in yellow) will appear on the Status bar.
Fixed a problem when a BRX CPU is configured as a multi-drop Modbus Slave that caused excessive retrys.
Fixed a problem that caused Axis Home Search (AXHOME) to not complete properly in firmware version 2.3.1.
Fixed a problem where the filter coefficient was not always applied properly in
the Filter instruction.
|2.3.1||13 Jun 2018||
Fixed a problem that caused Axis Home Search (AXHOME) and Axis Velocity Mode (AXVEL) to not work properly in firmware version 2.3.0.
Improved error reporting in EMAIL when any of the To, Cc, or Bcc addresses are invalid.
|2.3.0||31 May 2018||
Added support for BX-DMIO and BX-EBC100 as Ethernet Remote I/O Slaves.
Also added BX-MBIO - Modbus TCP / RTU Slave.
|1.0.3||2.2.1||10 Apr 2018||
Added Fixed a problem that would prevent a project that included a BACKUP - System Backup instruction from downloading to a BRX CPU.
|1.0.2||2.1.0||20 Sept 2017||
Added support for the following analog I/O modules:
BX-08AD-1 : 8 Channel Current Input
BX-08DA-1 : 8 Channel Current Output
BX-08AD-2B : 8 Channel Voltage Input
BX-08DA-2B : 8 Channel Voltage Output
BX-04THM : 4 Channel Thermocouple Input
Added the following instructions:
BACKUP - Create PLC Image File
COPY - Copy Data
DEBOUNCE - Reduce Discrete Input Chatter
FLASHER - Cycle Output On / Off
TIMEDOUT - Timed Output
Can now use the micro-SD card to backup and load projects using Create PLC
Image (BACKUP) instruction and / or Do-more Designer utility.
Fixed an error in the EMAIL instruction which was incorrectly
handling semicolons in the "To:" field.
Changed Axis Jog (AXJOG) so that inadvertent writes to the Axis' .TargetVelocity would not affect the Jog operation.
Fixed a problem where sometimes a communication failure would abort the download of the system configuration.
Fixed a problem that would prevent the CPU from going into
Debug mode if an Interrupt Service Routine is running.
|1.0.1||2.0.3||26 Apr 2017||
Added support for ECOMLT POM so that it can operate as
Modbus/TCP server, K-Sequence server, DirectNET server, or peer-to-peer with
an ECOM. Requires ECOMLT firmware version 4.0.145 or
later which is available through Live Update in NetEdit.
Adds noise filtering to the on-board serial port.
|2.0.2||22 Feb 2017||
Fixed problem that could cause spurious interruption of the
pulse train in the Axis following modes (AXGEAR, AXFOLLOW, AXCAM).
Fixed a problem in the module discovery that could cause a Fatal error during a project download.
Fixed a problem in the symbolic driver that could wrongly NAK good communication requests.
Fixed a problem in the serial communication driver that
would cause it to become unresponsive if the PLC is generating a lot of
|2.0.1||20 Feb 2017||
AXGEAR (Axis Electronic Gearing) renormalizes each time the
gear ratio changes.
Set a proper minimum Input
Filter value for 24V AC / DC inputs on the BX-DM1x-10 units.
|1.0.0||2.0.0||2 Feb 2017||Initial Release|